{"all":[{"note":"","secondTag":"","unit":"","firstTag":"技术参数","inputMode":"D1","infoPointName":"负荷级别","dataType":"Enum","infoPointCode":"LoadLev","func-id":"","priority":"S","dataSource":[{"code":"1","name":"一类：需要不间断供电"},{"code":"2","name":"二类：备用的供电系统"},{"code":"3","name":"三类：一般用户"},{"code":"99","name":"其他"}]},{"note":"","secondTag":"","unit":"","firstTag":"技术参数","inputMode":"D1","infoPointName":"关联电器工作制度","dataType":"Enum","infoPointCode":"EquipScheduleType","func-id":"","priority":"S","dataSource":[{"code":"1","name":"不间断"},{"code":"2","name":"工作时间"},{"code":"3","name":"非工作时间"},{"code":"4","name":"短时"},{"code":"99","name":"其他"}]},{"note":"","secondTag":"","unit":"A","firstTag":"技术参数","inputMode":"A2","infoPointName":"配电支路额定电流","dataType":"Num","infoPointCode":"RatedBrI","func-id":"","priority":"M","dataSource":""},{"note":"","secondTag":"","unit":"kW","firstTag":"技术参数","inputMode":"A2","infoPointName":"设计安装功率","dataType":"Num","infoPointCode":"DesignP","func-id":"","priority":"S","dataSource":""},{"note":"保护电流","secondTag":"","unit":"A","firstTag":"技术参数","inputMode":"A2","infoPointName":"继电器过电流值","dataType":"Num","infoPointCode":"RelayOverI","func-id":"","priority":"M","dataSource":""},{"note":"","secondTag":"","unit":"A","firstTag":"技术参数","inputMode":"A2","infoPointName":"断路器动作电流","dataType":"Num","infoPointCode":"BreakerActionI","func-id":"","priority":"M","dataSource":""},{"note":"","secondTag":"","unit":"","firstTag":"技术参数","inputMode":"G4","infoPointName":"关联设备","dataType":"Objects","infoPointCode":"RelatedEquip","func-id":"","priority":"R","dataSource":""},{"note":"","secondTag":"","unit":"","firstTag":"技术参数","inputMode":"D1","infoPointName":"开关柜类型","dataType":"Enum","infoPointCode":"CabType","func-id":"","priority":"R","dataSource":[{"code":"1","name":"固定面板式"},{"code":"2","name":"防护式"},{"code":"3","name":"抽屉式"},{"code":"99","name":"其他"}]},{"note":"","secondTag":"","unit":"个","firstTag":"技术参数","inputMode":"A2","infoPointName":"配套低压开关柜数量","dataType":"Num","infoPointCode":"LUCabNum","func-id":"","priority":"M","dataSource":""},{"note":"","secondTag":"","unit":"","firstTag":"运行参数","inputMode":"L","infoPointName":"运行状态","dataType":"Boolv","infoPointCode":"RunStatus","func-id":"","priority":"S","dataSource":[{"code":"0","name":"停止"},{"code":"1","name":"运行"}]},{"note":"","secondTag":"","unit":"","firstTag":"运行参数","inputMode":"L","infoPointName":"故障状态","dataType":"Boolv","infoPointCode":"FaultStatus","func-id":"","priority":"S","dataSource":[{"code":"0","name":"正常"},{"code":"1","name":"故障"}]},{"note":"","secondTag":"","unit":"","firstTag":"运行参数","inputMode":"L","infoPointName":"本地远程状态","dataType":"Enumv","infoPointCode":"RemoteStatus","func-id":"","priority":"S","dataSource":[{"code":"1","name":"本地"},{"code":"2","name":"BA"},{"code":"3","name":"云端"},{"code":"99","name":"其他"}]},{"note":"","secondTag":"","unit":"","firstTag":"运行参数","inputMode":"L","infoPointName":"手自动状态","dataType":"Boolv","infoPointCode":"ManualAutoStatus","func-id":"","priority":"S","dataSource":[{"code":"0","name":"手动"},{"code":"1","name":"自动"}]},{"note":"","secondTag":"","unit":"V","firstTag":"运行参数","inputMode":"L","infoPointName":"A相支路电压","dataType":"Inst","infoPointCode":"APhaseBrU","func-id":"","priority":"S","dataSource":""},{"note":"","secondTag":"","unit":"V","firstTag":"运行参数","inputMode":"L","infoPointName":"B相支路电压","dataType":"Inst","infoPointCode":"BPhaseBrU","func-id":"","priority":"S","dataSource":""},{"note":"","secondTag":"","unit":"V","firstTag":"运行参数","inputMode":"L","infoPointName":"C相支路电压","dataType":"Inst","infoPointCode":"CPhaseBrU","func-id":"","priority":"S","dataSource":""},{"note":"","secondTag":"","unit":"V","firstTag":"运行参数","inputMode":"L","infoPointName":"支路电压","dataType":"Inst","infoPointCode":"BrU","func-id":"","priority":"S","dataSource":""},{"note":"","secondTag":"","unit":"A","firstTag":"运行参数","inputMode":"L","infoPointName":"A相支路电流","dataType":"Inst","infoPointCode":"APhaseBrI","func-id":"","priority":"S","dataSource":""},{"note":"","secondTag":"","unit":"A","firstTag":"运行参数","inputMode":"L","infoPointName":"B相支路电流","dataType":"Inst","infoPointCode":"BPhaseBrI","func-id":"","priority":"S","dataSource":""},{"note":"","secondTag":"","unit":"A","firstTag":"运行参数","inputMode":"L","infoPointName":"C相支路电流","dataType":"Inst","infoPointCode":"CPhaseBrI","func-id":"","priority":"S","dataSource":""},{"note":"","secondTag":"","unit":"A","firstTag":"运行参数","inputMode":"L","infoPointName":"支路电流","dataType":"Inst","infoPointCode":"BrI","func-id":"","priority":"S","dataSource":""},{"note":"","secondTag":"","unit":"kW","firstTag":"运行参数","inputMode":"L","infoPointName":"支路功率","dataType":"Inst","infoPointCode":"BrP","func-id":"","priority":"S","dataSource":""},{"note":"","secondTag":"","unit":"kWh","firstTag":"运行参数","inputMode":"M","infoPointName":"累计用电电能","dataType":"Acc","infoPointCode":"AccE","func-id":"","priority":"S","dataSource":""}]}